Water is the source of life and plays a vital role in the industrial water treatment of society. Water is indispensable in industrial production. But now because of environmental pollution, water resources have not reached the level of industrial production, so the types of water has become multifarious, different water quality will be different for the quality of product production.
Many manufacturers choose chongqing ro reverse osmosis equipment to treat water. Chongqing ro reverse osmosis equipment adopts imported configuration elements and first-class technology to ensure the effluent quality of the equipment and the working efficiency of the equipment, meeting the water demand of different industries.
Role of chongqing ro reverse osmosis equipment:
1. The main function of media filter is to remove suspended substances and mechanical impurities in raw water. The equipment is made of high quality stainless steel. The body is equipped with cloth water cap, refined quartz sand and other fillers. Reasonable quartz sand filling proportion and good water distribution system make the water quality more stable. In addition, the equipment is equipped with the function of gas scour, which can remove dirt on the media and the bed to the maximum extent, improve the water quality and extend the working cycle.
2, activated carbon filter with deodorization, color removal, oil removal, adsorption of organic impurities and other functions, can maximize the removal of free residual chlorine in water, ensure the quality of reverse osmosis membrane inlet water, the equipment is made of high-quality stainless steel material.
3. RO main engine system introduces the international advanced reverse osmosis technology and utilizes the pressure difference principle to effectively remove the salt in the water, and the desalination rate can reach about 99%.
4. The mixed bed system adopts ion exchange technology and is equipped with Yin and Yang resins. The reasonable height of resin layer can effectively ensure the effluent water quality to meet the user's requirements.
Maintenance description of chongqing ro reverse osmosis equipment:
Chongqing ro reverse osmosis equipment
1. When the machine is shut down at night, the quartz sand filter and activated carbon filter can be backwashed with tap water as raw water. Because there is a certain pressure tap water, can still be through the pressure pump pump body and return valve into the sand filter and carbon filter.
2. According to the raw water quality and equipment operation, the operation cycle and time of the automatic water softener can be set according to the needs of users.
3, sand filter or carbon filter quartz sand or activated carbon, it is recommended to clean or replace a year or half a year or so.
4. Drain water once a week. Clean PP filter element in the fine filter once every 1 to 3 months. It is suggested to replace it every six months.
5. If the water yield is gradually reduced by 15% due to factors other than temperature and pressure, or the water quality gradually drops beyond the standard, then the reverse osmosis membrane needs to be cleaned chemically.
6. During the operation of chongqing ro reverse osmosis equipment, some faults may occur due to various reasons. After the problems occur, the operation records should be checked in detail to analyze the causes of the faults.